Ac Breaker Box Wiring
At the top of the breaker box the switch that s bigger than the others is commonly referred to as the main technically it s called the double pole service disconnect this is where after.
Ac breaker box wiring. Don t forget to subscribe thnx. Hooking up disconnect box conduit connectors and pull wires. How to and tips on mounting to masonry. The assumption here is that the utility has shut off the power to the feeder wires temporarily while the panel is installed and the hookups are made.
Overview wiring up a mini split hvac unit is not difficult but does require some basic electrical knowledge. With this done the cover can be put back on the ac s electric box. Wiring an a c unit involves installing a double pole 240 volt circuit breaker in the main service panel running a 240 volt cable to the a c s location installing a safety disconnect switch there and then running weatherproof flex from the switch to the a c s terminal box. Does not show install of breaker.
The disconnect switch is shown in figures 5 6 and 7. The wires can now be connected to their respective terminals inside the ac s electrical box by matching their colors with the colors of the wires already in place. Your electrician s first step will be to mount the breaker box to the wall of the utility area where the main service wires are located.